1 Answer. No — the 2014 NEC only calls out AFCIs for 120V, 15 and 20A outlets — the dryer is 240V, so it doesn’t need an AFCI. 210.12 Arc-Fault Circuit-Interrupter Protection. Arc- fault circuit-interrupter protection shall be provided as required in 210.12(A) (B), and (C).
Do appliances need to be on AFCI breaker?
Yes, you need AFCI protection
This includes dedicated appliances such as furnaces and dishwashers, and even smoke detector circuits.
What does not have to be AFCI protected?
Circuits supplying less than 120 volts (e.g., 24-volt control wiring, 12-volt lighting, telephone- or TV-signal wiring) are also exempt from AFCI protection.
Does a dryer circuit need to be GFCI protected?
First, receptacles installed to serve kitchen countertops must be GFCI protected. … Therefore, clothes dryers are now required to be GFCI protected because they are in the laundry area.
What circuits have to be AFCI protected?
As of the 2014 NEC, AFCI protection is required on all branch circuits supplying outlets or devices installed in dwelling unit kitchens, along with the 2008 NEC additions of family rooms, dining rooms, living rooms, parlors, libraries, dens, bedrooms, sunrooms, recreation rooms, closets, hallways, laundry areas, and …
Are refrigerators required to be AFCI protected?
A modern refrigerator requires a dedicated 20-amp, 120/125-volt circuit. … This circuit usually does not require GFCI protection unless the outlet is within 6 feet of a sink or located in a garage or basement, but it generally does require AFCI protection.
Where are AFCI breakers required 2020?
In the 2020 edition of the NEC®, Section 210.12 requires that for dwelling units, all 120-volt, single-phase, 15- and 20-ampere branch circuits supplying outlets or devices installed in dwelling unit kitchens, family rooms, dining rooms, living rooms, parlors, libraries, dens, bedrooms, sunrooms, recreation rooms, …
Do I need both GFCI and AFCI?
No. The latest National Electrical Code requires both AFCI and GFCI protection only in kitchens and laundry rooms. … If the Dual Function AFCI/GFCI replaces the first receptacle in the branch circuit, it will provide protection to the remaining outlets on that circuit.
Do outdoor outlets need to be AFCI?
AFCI protection is not required for outlets located outside or in garages or bathroom areas.
What rooms dont require AFCI?
Usually, this will include bedrooms, living rooms, dining rooms, etc. Some areas do not require AFCI protection provided GFCI protection is present. These include clothes washers, dishwashers, refrigerators, and bathrooms with a dedicated GFCI electrical outlet or circuit.
Which location is not required to be GFCI protected?
GFCI protection is not required for receptacles that are not readily accessible, such as a ceiling-mounted receptacle for a garage door opener. Nor are they required for a receptacle on a dedicated branch circuit located and identified for a cord-and-plug-connected appliance, such as a refrigerator or freezer.
Can you plug a washer and dryer into the same outlet?
In the Laundry Room
Your laundry room should have a dedicated circuit of at least 20 amps. If you have a gas dryer, both your washing machine and gas dryer may be plugged into the same outlet. If you have an electric dryer, it will need its own dedicated 20-amp, 220-volt circuit.
What appliances need a dedicated circuit?
Appliances that need a dedicated circuit include:
- Electric ranges.
- Wall ovens.
- Large Microwaves.
- Garbage disposals.
- Toaster ovens.