All 125-volt, single-phase, 15- and 20-ampere receptacles installed to serve the countertop surfaces in kitchens must be GFCI protected. … While the receptacle serving the countertop surface requires GFCI protection, the other receptacle does not.
Do all outlets in kitchen need to be GFCI?
All countertop receptacle outlets must be protected by a GFCI device installed at the outlet or by GFCI circuit breakers. A kitchen must have two 20-amp circuits for countertop appliances. There should be countertop receptacles installed so that no point along the counter is more than 2 ft. from an outlet.
Which receptacles in the kitchen must have GFCI protection?
Kitchens: All receptacles serving countertop areas and any receptacle within 6 feet of a sink must have GFCI protection. … Laundry, utility, and wet bar sinks: Where receptacles are placed within 6 feet of the outside edge of the sink, they require GFCI protection.
How many outlets can 1 GFCI protect?
There’s no limit. A standard GFCI will protect up to 20 amps, drawn from any combination of receptacles, either the built-in one or any number of additional ones connected to its load terminals.
What is code for outlets in kitchens?
In kitchens, electrical outlets should be placed no farther than 48 inches apart, so that no point on the countertop is more than 24 inches away from a receptacle. Any countertop 12 inches wide or more should have an outlet on the wall behind the countertop.
What’s the difference between GFI and GFCI?
Ground fault circuit interrupters (GFCI) and ground fault interrupters (GFI) are the exact same device under slightly different names. Though GFCI is more commonly used than GFI, the terms are interchangeable.
Should a fridge be on a GFCI?
Should a refrigerator be plugged into a GFCI outlet? A refrigerator shouldn’t be plugged into a GFCI outlet. GFCI outlets are used in areas of the home with water or moisture. … The problem with refrigerators is that they can cause unneeded trips in GFCI outlets.
Should I get a 15 or 20 amp GFCI outlet?
Look at the GFCI you are replacing. … Kitchens and bathrooms should always have 20 amp gfci outlets. However, you must be using number 12 wire for 20 amp gfci or regular outlets If your wiring is number 14 guage then use a 15 amp. So, the wire size and breaker size together should be rated for 20 amps!
Can you put 2 GFCI outlets on the same circuit?
Yes, you can use two or more GFCI outlets on the same circuit without any problem at all. The only downside to this is that if one of your GFCI outlets goes down, the others will probably go down as well. … It is well worth putting two or more GFCI outlets on the same circuit, and it’s quite common.
Can I put a GFCI anywhere in a circuit?
You can replace almost any electrical outlet with a GFCI outlet. Correctly wired GFCIs will also protect other outlets on the same circuit. … The electrical code also requires GFCIs in unfinished basements, garages, most outdoor receptacles and places where construction activity occurs.
Which location is not required to be GFCI protected?
GFCI protection is not required for receptacles that are not readily accessible, such as a ceiling-mounted receptacle for a garage door opener. Nor are they required for a receptacle on a dedicated branch circuit located and identified for a cord-and-plug-connected appliance, such as a refrigerator or freezer.
How much does it cost to install a GFCI outlet?
Install a GFCI Outlet: national average cost
The national average materials cost to install a gfci outlet is $19.71 per receptacle, with a range between $17.68 to $21.74. The total price for labor and materials per receptacle is $154.04, coming in between $140.26 to $167.83.